Back to top
Using Maple Systems EZWare Plus to AKD or AKD BASIC
Note: I don’t have EzWare Plus software or the HMI and no specifics on software revisions or HMI hardware revisions or models. I have no sample project.
The following is based on what worked and was learned through support.
If a data field is declared as 32 bit in the Maple and you are trying to read an AKD parameter or AKD BASIC variable, the Maple needs an offset of 1 from the WB Help starting address and also word swapping.
For example in the AKD BASIC program
Dim myVariable1, myVariable2 as integer MBInfo $MBMap32(5000, myVariable1) $MBMap32(5002, myVariable2) End
We set the Maple Systems data field for the data in myVariable1 to be a signed 32 bit integer and the addressing was 5x 5001….there is a 4x method without word swapping but the 5x swaps the high and low words ( per below and the Modbus Controller Datasheet; see attached ).Maple stated they are high word first ( like the AKD ) but it was counterintuitive. In any case, the use of the 5x register type and the offset of 1 ( 5000+1 ) allowed the HMI to display a 32 bit value correctly.