Back to top
AKD EthernetIP communication with Omron PLC problem
When import EIP.EDS file to Omron PLC, the PLC output start address is D200, input start address is D100, and Ethernet_IP manual did not tell us the sequence of
control , what's the right code of Position mode and Jog mode?
Submitted by engao cui Mon, 06/15/2015 - 08:08
We are not familiar with programming an Omron PLC. The Omron people have written a user manual for setup and operation of the AKD and Omron PLC. I do know the Omron and AKD will only work in Cyclic Synchronlusposition mode. Jogging motion profile will have to be 100% generated in the PLC.
Submitted by [email protected] Fri, 06/19/2015 - 05:10